The product is a new energy-saving switch, it adopts integrated circuit and the good sensitivity detector. It gathers automatism, convenience, safety, energy-saving and practicality function. The wide detection range is made up of the up and down, left and right service field. It works by receiving human motion infrared rays. It can start the controlled load at once when one enters the detection field. It can identify day and night automatically. Its using range is wide. It has the functions of the power indication and the detection indication.
• Power source: 100V/AC~130V/AC
• Power frequency: 50~60Hz
• Ambient light: <10LUX~2000LUX
• Time-Delay: min: 8sec±3sec
• Max: 7min±2min Detection range: 120°
• Detection distance: 9m max (<24℃)
• Rated Load: 400W (110V/AC~130V/AC)
• 600W (220V/AC~240V/AC)
• Working temperature:-20~40℃
• Working humidity :< 93%RH
• Installation height: 1m~1.6m
• Power consumption: 0.45W(static 0.1W)
➢ Detection field: The detection field is made up of up and down, left and right service field. (See the following diagram ). But the moving orientation has great relationship with the sensitivity.
➢ Can identify day and night: The ambient light can be adjusted according to the
consumer’s desire , when it is adjusted on the “moon” “position (min), it can only work in the less than 10LUX ambient light; It can work in the daytime and at night when it is adjusted on the “sun” position (max); As for the adjustment pattern, please refer to the testing pattern;
➢ Time-delay is added continually: When it receives the second induction signals after
the first induction, it will compute time once more on the rest of the first time-delay basic.(set time)
➢ Time-delay is adjustable: It can be set according to the consumer’s desire. The minimum time is 8sec±3sec. The maximum is 7min±2min.
➢ The switch: It is the “auto” condition when you push it in. It is “OFF” condition when you push it out.
INSTALLATION: (see the following diagram)
➢ Switch off the power
➢ Take off the sensor board-face and the nail.
➢ Connect the power and the load wire with the sensor according to connection-wire diagram
➢ The sensor is fixed on the selected position.
➢ You can switch on the power and test it after covering the board-face.