The product is a new saving-energy switch adopting the good sensitivity detector, integrated circuit and SMT. It gathers automatic, convenient, safe, saving-energy and practical functions. The wide detection field is made up of up and down, left and right service field. It works by receiving human motion infrared rays. When one enters the detection fields, it can start the load at once and identify day and night automatically; It can be used with various types of lamps and lanterns.
Power source: 220-240V/AC
Power frequency: 50Hz
Rated load: 300W Max.tungsten
Time setting: (8±2)S-(6±2)Min (adjustable)
Light-control: <10LUX~2000LUX (adjustable)
Detection range: 8m Max (dia.) (adjustable)
Detection angle: 360°
Installation height: 2.5m~3.5m
Working temperature: -10~+40°C
Detection motion speed: 0.6~1.5m/s
Working humidity: <93%RH
Standby power: 0.45W(static 0.1W)
➢ Detection field: the detection field is made up of up and down, left and right service field, it can be selected according to the consumer’s desire. But the moving orientation has great relationship with the sensitivity.
➢ Can identify day and night: the light control can be adjusted freely when it works. It can work in the daytime and at night when it is adjusted on the “sun” position (max); but it can only work in the light control less than
10lux when it is adjusted on the “moon” position (min). As for the adjustment pattern, please refer to the testing pattern.
➢ Time delay can be added continually: when it received the second induction signal after the first it will
compute time once more on the rest of the first time delay basic.(Set time)
➢ Light-control potentiometer (LUX): clockwise the knob to increase its value; anti-clockwise the knob to decrease its value.
➢ Time potentiometer (TIME): clockwise the knob to increase its value, the maximum delay time is (6±2)
minutes; anti-clockwise the knob to decrease its value, the minimum delay time is (8±2) seconds.
➢ Sensitivity potentiometer (SENS): clockwise the knob to increase its value, the maximum distance is 8m(dia.).
Installation (see the following diagram)
➢ Switch off the power.
➢ Set threaded tubes into the power cord and control line.
➢ Connect the power and the load with the sensor according to the connection-line diagram.